Was ist die F-Gase Verordnung?
Installations containing less than 3 kg of fluorinated greenhouse gases or hermetically sealed equipment containing less than 6 kg of fluorinated greenhouse gases shall not be leak tested.
All systems with a CO2 equivalent of more than 5 tons and less than 50 tons must be checked for leaks once every 12 months (obligation of the operator).
The use of refrigerants with a GWP greater than 2500 in installations with cryogenic temperatures greater than -50 °C is prohibited. These refrigerants may still be used in systems with a minimum temperature of less than -50 °C. The use of refrigerants with a GWP greater than 2500 in systems with a minimum temperature of less than -50 °C is prohibited.
The F-Gas regulation is valid in all countries of the European Union. All equipment sold in this region must comply with the applicable regulations.
Ziel der F-Gas Verordnung
The Regulation aims to limit the global temperature increase to 2 °C in order to avoid undesirable climate impacts. CO2 emissions from industry are to be reduced by up to 73% by 2030 compared with 1990 levels. To achieve the target, the estimated CO2 equivalent must be reduced from 104 million tonnes in 2030 to about 35 million tonnes.
FAQ on the F-gas regulation
When is a leak test necessary?
For systems that use a refrigerant with a CO2 equivalent between 5 t and 50 t, a leak test must be carried out every 12 months. This is the duty of the operator of the plants.
Which products are covered by the F-Gas regulation?
The F-Gas regulation includes all refrigeration devices that use a refrigerant that has a GWP> 2500.
What does GWP mean?
The global warming potential (GWP) of a chemical compound is a measure of the relative effect of the contribution to the greenhouse effect.
What does CO2 equivalent mean?
The CO2 equivalent is the product of the GWP of the refrigerant times the filling quantity in the respective system.